Supply of Cable Glands of various sizes.
||1) Cable glands shall be Double compression type, tinned/Nickel plated (coating thickness not less than 20microns in case of tin and 10 to 15 microns in case of nickel) brass cable glands for all power and control cables.
2) They shall provide dust and weather proof terminations.
3) They shall comprise of heavy-duty brass casting, machine finished and tinned to avoid corrosion and oxidation. Rubber components used in cable glands shall be neoprene and of tested quality. Required number of packing glands to close unused openings in gland plates shall also be provided.
4) The cable glands shall be tested as per BS: 6121. The cable glands shall also be duly tested for dust proof and weather proof termination.
Materials to be delivered within 60 days of award of order.